Voltage Drop Calculation Method
|Up Previous Next|
Three-Phase % Voltage Drop = Load in Amps * Effective Z * (Wire Length / 1,000) * 100 / Line-to-Neutral Voltage
Single-Phase % Voltage Drop = Load in Amps * Effective Z * (Wire Length / 1,000) * 100 * 2 / Voltage
Load in Amps is different for feeders and branch circuits. For feeders, it is the calculated load on the panel assuming a balanced load. For branch circuits, it is based upon the connected load.
Effective Z = R * Power Factor + X sin (acos(Power Factor)) (See NEC Table 9 Note 2)
R = Resistance set in the command.
X = Reactance set in the command.
Power Factor = 0.85
Line-to-Neutral Voltage is used for three-phase calculations based upon NEC Table 9 Note 2: "Multiplying current by effective impedance gives a good approximation for line-to-neutral voltage drop."
Voltage is the line-to-neutral voltage for single pole circuits and line-to-line voltage for two pole circuits.
The feeder impedance values are based upon NEC Table 9. These values can be modified by the user.
The transformer impedance values are for dry-type indoor transformers. These values can be modified by the user.
©2012-2018 Design Master Software, Inc