Fault Calculation Basis
|Up Previous Next|
The fault calculations are based upon IEEE Std 242-2001: IEEE Recommended Practice for Protection and Coordination of Industrial and Commercial Power Systems.
The fault that is calculated is the three-phase line-to-line fault.
Fault = Voltage / √(Resistance2 + Reactance2)
The fault calculation includes motor contributions for all devices that have the Load Sub-Classification Motor Revit parameter enabled. This parameter is set on the connector element of the device family, in the Electrical - Loads section of the Properties panel.
The Circuit Length from the motor to the panel is accounted for. By default, the motor current is equal to 4 times the rated current of the motor and the X/R ratio of motors is 4. These values can be modified using the command or command.
The fault is not calculated for circuits that have more than one branch circuit device connected.
The feeder impedance values are based upon NEC Table 9. These values can be modified by the user using the command.
The transformer impedance values are for dry-type indoor transformers. These values can be modified using thecommand or command.
©2013-2022 Design Master Software, Inc