Wall Project Schedule
|Up Previous Next|
The wall project schedule contains the wall types available to be used in the current project.
To create and modify wall types, go to
DM HVAC->Building Definition->Schedules->Wall Project Schedule
Wall Project Schedule Dialog Box
See the Rename, Find, Previous, Next, New, Copy, Save and Delete buttons.section for more information about how this dialog box works. This section describes the
See theand pages for more information about importing wall types to the current project from other locations.
Wall Type: The name of the wall type.
U-Value: The heat transfer coefficient of the wall.
ASHRAE Wall Type: The type of wall used to determine the rate of solar heat transfer through the wall. The CLTD method is based upon 15 different walls types, numbered from 1 to 16 (skipping 8). The walls are roughly ordered so that type 1 is the lightest construction and type 16 is the heaviest. Heat is transferred more quickly through light walls. Heavy walls absorb the heat and release it into more slowly into the room.
The wall types are defined in Table 33A in 1997 ASHRAE Fundamentals Handbook, pages 28.46 - 28.48.
Color: The color of the wall. It is recommended by the CLTD method that you choose Dark and not adjust the wall load based upon the color.
Description: A longer description of the wall type. Displayed when selecting the wall type and in the Wall Types table of the Building Definition print out.
©2012-2013 Design Master Software, Inc