You are here: Home > Support > Knowledge Base > Arc-Flash Trip Times

## Arc-Flash Trip Times

Tuesday, January 19th, 2016

When using Design Master Electrical to calculate arc-flash values, you must specify the trip time for the breakers. These values are based upon the time-current curve for the specific breakers that will be installed in your project.

Often, you don’t know what breakers are going to be used or are unable to obtain the curves for them. Here is a general method you can use for determining the trip time in those situations.

For each piece of equipment, locate the upstream overcurrent protection (OCP). This OCP needs to be outside the equipment. For example, do not use the main breaker for the panel. Instead, use the breaker in the panel upstream.

Note the size of the OCP and the rating of the OCP.

For a breaker, multiply the rating by 10. For a fuse, multiply the rating by 5. Compare that number to the arcing current value calculated by Design Master Electrical.

If the arcing current is greater than that value, set the arcing time to 0.0167. The OCP will trip immediately in this case, which requires 1 cycle.

If the arcing current is less than that value, set the arcing time to 2. The OCP will effectively never trip. A maximum of 2 seconds is used because we assume the individual will move out of the arc in that time.

### Related Articles

This training video shows you the new features introduced and improvements made in Design Master Electrical RT 2.0.

8

If you’re thinking about moving your electrical workflow to Revit, here are the concepts you’ll need to research before you get started.

8

There are several factors that can influence arc-flash calculations, such as the working distance and the electrode configuration.

8

Review the basics of arc-flash calculations, then look at how to perform them in Design Master Electrical RT.

0

This one command has a lot of little features packed into it. See how you can take advantage of them in your projects.

0

Design Master does not offer 4-pole voltage options for transfer switches; however, you can safely model them using a 3-pole voltage and notes.

0

Products

Electrical for Revit