You are here: Home > Support > Knowledge Base > NEC 220.55 for Single-Phase Ranges and Three-Phase Service

## NEC 220.55 for Single-Phase Ranges and Three-Phase Service

Thursday, December 26th, 2019

Q: My project has single-phase ranges supplied by a three-phase panel. My manual load calculation for the ranges based upon NEC 220.55 doesn’t match Design Master’s calculation. How is the load being calculated?

A: This calculation has several moving parts, including one that is not explicitly mentioned inĀ NEC 220.55 itself but is shown in Annex D, Example D5(a). This article will provide another example with some additional context. Relevant information about the project is as follows:

 # of Ranges, Phase A-B 28 # of Ranges, Phase B-C 20 # of Ranges, Phase C-A 24 Connected Load per Range 9.1 kVA

1. Find the maximum number of ranges between any two phases.
In this example, phase A-B has the most ranges at 28.
2. Multiply that number by 2.
28 ranges * 2 = 56 ranges
3. Using that number, calculate the demand based upon NEC Table 220.55.
This example will use Column C (rating between 8.75 and 12 kVA). For 56 ranges, the demand is 25 kVA plus 0.75 kVA for each range.
25 kVA + (0.75 kVA * 56 ranges) = 67 kVA
4. Divide that number by 2 to calculate the single-phase load.
67 kVA / 2 = 33.5 kVA
5. Multiply that number by 3 to calculate the three-phase load.
33.5 kVA * 3 = 100.5 kVA

The panel schedule footer will display the connected load and number of ranges for each phase, as well as the calculated load, rounded to the nearest integer (in this case, 101 kVA):

### Related Articles

This video provides an example of how to customize a panel schedule in Design Master Electrical.

8

You can balance the loads on panels using the Move Circuits command.

8

This training video teaches you how to use the Circuiting command in Design Master Electrical.

8

This training video teaches you how to disconnect distribution equipment, configure feeder and service loads, and more in Design Master Electrical for AutoCAD.

0

Here are a few ways you can continue using Design Master collaboratively on projects while working remotely.

0

This training video teaches you how to create devices and modify schedules for future projects, create and customize combined homeruns, and more in Design Master Electrical for AutoCAD.

0

Products

Electrical for Revit