You are here: Home > Support > Knowledge Base > Wire Ampacity Changes in DM Electrical RT 2.0

## Wire Ampacity Changes in DM Electrical RT 2.0

Tuesday, August 17th, 2021

We added two new fields to the Wire Ampacities command in DM Electrical RT 2.0. These values were added to handle calculations for derating wire due to ambient temperature and more than 4 conductors in a conduit.

When projects created using previous versions are updated to the new version, default values are provided for these two fields. The default values are conservative. If you plan to use the new calculations and want more precise calculations, you will need to update these values in your project.

### Wire Ampacity @ 30°C

Previously, the dialog box only listed Breaker Ampacity. It was assumed the wire ampacity was as large as or larger than the breaker ampacity. For derating calculations, however, the software needs the actual ampacity of the wire itself.

When a project is converted, the Wire Ampacity @ 30°C values are set equal to the Breaker Ampacity divided by the Parallel Runs. That value is conservative; there are cases where the wire ampacity will be higher.

For example, a 50A Breaker Ampacity is set to use #6 wire. When the project is converted, the Wire Ampacity @ 30°C will default to 50A. However, per NEC Table 310.16, the correct value is 55A.

### Temperature Rating of Conductor

This value is used for derating calculations due to ambient temperature based upon NEC Table 210.15(B)(1).

When a project is converted, the Temperature Rating of Conductor values are set to 60°C for #1 wire and smaller, and 75°C for 1/0 wire and larger.

If you have adjusted your wire sizes to assume different conductor temperature ratings, review these values to make sure they match.

### Related Articles

This framework will help you better understand how to model your electrical design in Revit.

24

This training video teaches you how to adjust conduit sizing and address irregularities with panel names in Design Master Electrical for Revit.

24

This video tutorial series shows how to perform basic tasks in Design Master Electrical RT.

24

This training video shows you the new features introduced and improvements made in Design Master Electrical RT 2.0.

24

This training video shows you the improvements made in Design Master Electrical RT 2.0 Beta 8.

24

If you’re thinking about moving your electrical workflow to Revit, here are the concepts you’ll need to research before you get started.

24

Products

Electrical for Revit

Electrical for AutoCAD

HVAC for AutoCAD

Photometrics for AutoCAD

System Requirements

19401 40th Ave W, Suite 302
Lynnwood, WA 98036

©2001-2021, Design Master Software, Inc