## Electrode Configurations for Arc-Flash Calculations

Posted on March 26th, 2019. Last updated on July 9th, 2019.

In order to calculate arc-flash for a piece of distribution equipment, you must set its electrode configuration as described in IEEE Std 1584-2018 Table 9.

This article illustrates each electrode configuration so you can determine the appropriate option for your distribution equipment.

## VCB

This image shows an example of a Vertical conductors or electrodes inside a metal box or enclosure configuration.

The conductors extend downward from the top of a metal box or enclosure.

This configuration typically results in lower incident energy values than other configurations except for VOA.

## VCBB

This image shows an example of a Vertical conductors or electrodes terminated in an insulating barrier inside a metal box or enclosure configuration.

The conductors extend downward from the top of a metal box or enclosure and terminate in an insulating barrier.

This configuration typically results in higher incident energy values than other configurations except for HCB.

## HCB

This image shows an example of a Horizontal conductors or electrodes inside a metal box or enclosure configuration.

The conductors extend outward from the back of a metal box or enclosure.

This configuration typically results in the highest incident energy values.

## VOA

This image shows an example of a Vertical conductors or electrodes in open air configuration.

The conductors extend downward and are not enclosed.

This configuration typically results in the lowest incident energy values.

## HOA

This image shows an example of a Horizontal conductors or electrodes in open air configuration.

The conductors extend outward and are not enclosed.

This configuration typically results in higher incident energy values than VOA and VCB, but lower than VCBB and HCB.

### Related Articles

There are several factors that can influence arc-flash calculations, such as the working distance and the electrode configuration.

14

Review the basics of arc-flash calculations, then look at how to perform them in ElectroBIM.

8

This one command has a lot of little features packed into it. See how you can take advantage of them in your projects.

8

Revit does not handle bus ducts well. There are a few different ways you can model them, each with different tradeoffs. We explore the options that are available and how the options impact single-line diagrams and calculations in ElectroBIM.

0

Learn about the new Generate One-Line command. This new command automatically drafts your one-line based on the panels in your Revit model. Learn about all the settings and configuration options that are included to guide the output of the

0

This training video teaches you how to adjust conduit sizing and address irregularities with panel names in Design Master Electrical for Revit.

0